02 9460 8881
- 0.36 KGS
Powerform's ROT4 series of run-on timers are primarily used for the residential apartment market. These automate the toilet/laundry/kitchen exhaust system to improve the amenity of apartments and reduce energy consumption. The ROT4 enables automatic fan run time based on the activation of multiple control circuits such as two separate lights and a washer/dryer which act as triggers. A typical application is a bathroom fan assisted air extraction system where activation / deactivation of the bathroom light for longer than the delay period, initiates the fan. When the light is switched OFF, the fan runs-on for the specified ‘run-on’ time.
Unlike the ROT6, the ROT4 doesn't include a current sensor & doesnt have any standby power
This feature delays turning the fan on until a certain number of seconds have passed. It is used so that a short visit to the bathroom doesn’t result in the fan “running on” (eg to brushteeth).
Range of Start Delay: immediate start - 210 second delay
Run On Range
This sets the range of the front mounted adjuster
Run on Range: 2-10min, 10-20min, 20-30min, 30-90min
If enabled the fan will run at full speed for 2 seconds when it turns on to ensure it starts properly and any backflow prevention devices are open
This enables the current sensor if it is fitted. Has no effect if it is not fitted.
This allows the resident to cancel the run on time by switching the input on for less than 1 second then off again. This may be desirable if they can hear the fan at night after a brief toilet visit
ROT4 Timer - 1 input, Inputs = terminals, Output = 3 pin socket. motor speed adjustment or current sensor
- ROT4V-1ip-T-S - 1 input, 3 pin socket, no motor speed control & no current sensor
- ROT4V-3ip-T-S - 3 input, 3 pin socket, no motor speed control & no current sensor
- ROT4V-3ip-T-S-Sp - 3 input, 3 pin socket, Motor speed control & no current sensor
- Australian made
- Start Delay
- Run on Range
- Fan Boost
- Current Sensor (if fitted)
- Timer Cancel
- RoHS and Ctick approved
- Easy to follow installation guide